Find great deals for Andover Controls Continuum NetController LL Cx Tac Inc.. Shop with confidence on eBay!. Andover Continuum™. Product Catalogue. Issue: October . Infinet NetController II CPU Module. Infinet NetController – Display Modules. NetController II Andover Continuum power supply or third-party UL Listed UL Be sure your Andover Continuum cabinet is connected to the ground.
|Published (Last):||8 August 2008|
|PDF File Size:||13.15 Mb|
|ePub File Size:||9.94 Mb|
|Price:||Free* [*Free Regsitration Required]|
I think that this is also database problem, because i think controller work in “NoDB” mode, but may be i wrong. I’m asking this question because I haven’t done it. In same network we have other controller Andover CX with them we have not problems. The Thrill of Exceeding Expectations. Then One Foggy Service Call First you have to go to the Menu bar forgot the term at the bottom right and find the controller ICON. But at a stage when I send blank controller to SQL database, in the distributions window i get error produced: This should reset the controller, wait for it to come back online, then send the system variables to the controller.
Andover Continuum NetController II – Feature Blast
Please can you tell me what could be the problem??? Training and Education Pro’s Forum: All three controllers are online and reply for ‘who is’ global broadcast.
Thanks for your help, as soon as possible i will try to do what you said. I could see my controllers online.
Valves, Regulators, Filters, Etc. Originally Posted by AutoPilot. If controller is functioning properly it should come back online totally blank. When you reload the controller, the proper path, and handle info is sent to the controller. Like you we have version 1. Even i tried to delete nw and everything which i have created. Subscribe to this feed. HVAC-Talk is proudly provided by: Andover Controls Net controller netconyroller.
Hello, I have a problem with Andover Controls Net controller: Results 1 to 10 of 10 Thread: The controller should be gone at this point. Ameya Hi Autopilot, I am new to the forum and I am looking solution for somewhat similar problem. nrtcontroller
But I woul like to try them. I’ve seen this problem before. The time now is After a successful import no errors you should be able to reload the controller without any problems.
Thanks you Very much.
Andover Controls Continuum NetController LL Cx Tac Inc. | eBay
Related Forums The place where Electrical professionals meet. Import the previously saved text file, Send to controller and all should good. Building Success with Routines and Rituals. Send the controller to the SQL database this, should be fairly quick as there are no programs or points in the controller. If all is netcontrkller, the controller will be ready to reconcile any handle issues it the text dump.
This is not a DIY board and what I suggested is not for the faint of heart. I have done some reloading, created points, revise the program but not this deep of situation If we evolve from the monkey then why are there still monkeys. If all is good at this point your controller is good.
If you get any errors during the netcontrolle import, you will need to correct them. Power Quality Pro’s Forum: I haven’t done what Autopilot has discribed. General Discussion Pro’s Forum: Results 1 to 10 of Ping to the controller always didn’t lost. It’s rare, difficult and time consuming to trouble shoot. Borias, From your question about netcontrollrr a text file I’m wondering if you have had any formal Continuum Training. I only do this on controllers that have the problem Borias described.
But problem still exists. I am using continuum version 1.